For fire prevention, maintenance and safety, it is best to use the national standard copper core wire. The wire slot area is generally: 1.5 square millimeters for lighting, 2.5 square millimeters for socket, and 2.5 square millimeters for air conditioning. Use 4 square millimeters), connect the negative line (neutral/ground) with green and yellow two-color lines, and connect the switch lines (fire lines) with red, yellow and blue. However, the color usage of the lines used in the same home improvement project should be consistent.
Type: PVC Insulated
Conductor Material: Copper Conductor
Insulation Material: PVC
Conductor: Copper Core
Rated Voltage: 300V/500V
Type: Stranded flexible
Color: Red, Green, Yellow, Blue, Black
Insulation: Double PVC
Rated voltage 450/750v and below pvc wire and cable
This product adapt to AC rated voltage (Uo/U)450/750 and below power, household appliances, instruments, small power tools, power lighting, etc.
1. Laying temperature ≥0℃
2. Cable woring temperature:the maximum working temperature of 60227IEC07(BV-90),60227IEC08(RV-90) is 90℃,other is 70℃.
3. Bending radius:D<25mm,should not less than 4D;D≥25mm,should not less than 6D.