1. This product is suitable for transmission and distribution lines with AC rated voltage of 0.6/1kV (Uo/U) and below. It can be laid indoors, outdoors, in the channel and concrete pipe group, or embedded in loose soil, and can not bear mechanical external force. Function, but can accept a certain amount of traction.
2. The maximum long-term working temperature of the cable conductor is 90 °C; when the short circuit (the longest duration does not exceed 5 s), the maximum temperature of the cable core does not exceed 250 °C.
3. The bending radius of the cable, the single-core cable is not less than 12 times the outer diameter, and the multi-core cable is not less than 10 times the outer diameter.
4. The cable laying temperature should not be lower than 0 °C.
|Insulation Material:PVC||Type:Low Voltage|
|Rated voltage:300/500 Volts|
The 450/750 V copper conductor EPR insulated rubber cable used for household electrical appliances, electrical tools, and various mobile electrical equipments.
Conductor: Stranded bare or tinned soft copper wire
Insulation: EPR (Ethylene-Propylene Rubber)
Sheath: Neoprene (Chloroprene rubber)
Rated Voltage: (Uo/U)
A. C. 450/750V (H07RN-F)